DAR File No. 42527
This rule was published in the February 15, 2018, issue (Vol. 2018, No. 4) of the Utah State Bulletin.
Health, Disease Control and Prevention, Environmental Services
Design, Construction and Operation of Public Pools
Notice of Proposed Rule
DAR File No.: 42527
Filed: 01/30/2018 11:05:13 AM
Purpose of the rule or reason for the change:
This amendment updates the list of authorizing statutes, fixes typos, and introduces a definition and a new section in response to comments from the Administrative Rules Review Committee.
Summary of the rule or change:
Nonsubstantive changes update the list of authorizing statute to include Subsection 26-1-30(9) and Section 26-7-1; add the inches equivalent for signage requirements in the new Subsection R392-302-38(2)(b); add a footnote to Table 6 reflecting the current language in Subsection R392-302-27(1)(b)(i); and fixed the numbering in Section R392-302-21. The change also fixes a typo in the new Subsection R392-302-39(3)(c) to require rules lettering to be 0.5 inches tall instead of 1.5 inches, and adds a definition of "Instructional Pool". Substantial revision have been made to the Special Purpose Pool Section R392-302-31. This has been divided into separate sections (R392-302-32, R392-302-33, R392-302-34, and R392-302-35) for each type of special purpose pool. A new Section R392-302-36 is added for Instructional Pools. Changes have been made throughout the rule to reflect the new section numbers.
Statutory or constitutional authorization for this rule:
- Section 26-1-5
- Section 26-15-2
- Subsection 26-1-30(23)
Anticipated cost or savings to:
the state budget:
There are no anticipated costs or savings to the state budget resulting from this rule change.
This rule change will affect new construction of a pool if it meets the requirements to be an instructional pool. This rule change does not require construction or operational changes to existing facilities. A local government building an instructional pool may have an approximate savings of 80% to 90% of the construction costs as compared to meeting the requirements of the current rule. The Department of Health (Department) is unable to estimate this benefit due to the wide range of possible costs involved (size, features, types of disinfectant, and plumbing, etc.). It is unlikely this rule change will have an ongoing cost or savings as the rule changes do not affect the operation of the pool.
There are an estimated 11 swim school or swim instruction businesses from NAICS 611620, 611710, and 812199. There are an estimated 61 small businesses affected by this rule from NAICS 541330, 561790, 541690, 425120, 238992, 238991, and 236220, but an inestimable number from NAICS 713990, 713940, 531311, and 721110 as these businesses may or may not have swimming pools, and there is no reasonable method of determining such. In FY17 there were 3,063 permitted facilities, but the data is not available to determine which of these are small or non-small businesses. This rule change will affect new construction of a pool if it meets the requirements to be an instructional pool. This rule change does not require construction or operational changes to existing facilities. A small business building an instructional pool may have an approximate savings of 80% to 90% of the construction costs as compared to meeting the requirements of the current rule. The Department is unable to estimate this benefit due to the wide range of possible costs involved (size, features, types of disinfectant, and plumbing, etc.). It is unlikely this rule change will have an ongoing cost or savings as the rule changes do not affect the operation of the pool.
persons other than small businesses, businesses, or local governmental entities:
There are an estimated 41 non-small businesses from NAICS 713990, 713110, 713940, but an inestimable number of large businesses with pool facilities from NAICS 531311 and 721110. In FY17 there were 3,063 permitted facilities, but the data is not available to determine which of these are small or non-small businesses. This rule change will affect new construction of a pool if it meets the requirements to be an instructional pool. This rule change does not require construction or operational changes to existing facilities. A non-small business building an instructional pool may have an approximate savings of 80% to 90% of the construction costs as compared to meeting the requirements of the current rule. The Department is unable to estimate this benefit due to the wide range of possible costs involved (size, features, types of disinfectant and plumbing, etc.). It is unlikely this rule change will have an ongoing cost or savings as the rule changes do not affect the operation of the pool.
Compliance costs for affected persons:
No one specific person will be affected by this rule change.
Comments by the department head on the fiscal impact the rule may have on businesses:
The proposed amendment is a response to comments made by the Legislature's Administrative Rules Review Committee in a recent hearing. The Special Purpose Pool section has been substantially revised. It was divided into separate sections for each type of a special purpose pool with the addition of a new section for Instructional Pools. There may be significant savings of 80% - 90% to a small business building an instructional pool but the Department is unable to estimate the benefit due to the wide range of possible costs involved (size, features, types of disinfectant, and plumbing, etc.).
Joseph K. Miner, MD, Executive Director
The full text of this rule may be inspected, during regular business hours, at the Office of Administrative Rules, or at:Health
Disease Control and Prevention, Environmental Services
CANNON HEALTH BLDG
288 N 1460 W
SALT LAKE CITY, UT 84116-3231
Direct questions regarding this rule to:
- Chris Nelson at the above address, by phone at 801-538-6739, by FAX at , or by Internet E-mail at firstname.lastname@example.org
Interested persons may present their views on this rule by submitting written comments to the address above no later than 5:00 p.m. on:
This rule may become effective on:
Joseph Miner, Executive Director
Appendix 1: Regulatory Impact Summary Table*
Total Fiscal Costs:
Total Fiscal Benefits:
Net Fiscal Benefits:
*This table only includes fiscal impacts that could be measured. If there are inestimable fiscal impacts, they will not be included in this table. Inestimable impacts for State Government, Local Government, Small Businesses and Other Persons are described above. Inestimable impacts for Non-Small Businesses are described below.
Appendix 2: Regulatory Impact to Non-Small Businesses
There are an estimated 41 non-small businesses from NAICS 713990, 713110, 713940, but an inestimable number of large businesses with pool facilities from NAICS 531311 and 721110. In FY17 there were permitted 3063 facilities, but the data is not available to determine which of these are small or non-small businesses.
This rule change will affect new construction of a pool if it meets the requirements to be an instructional pool. This rule change does not require construction or operational changes to existing facilities.
A non-small business building an instructional pool may have a savings of 80% to 90% of the construction costs as compared to meeting the requirements of the current rule. The Department is unable to estimate this benefit due to the wide range of possible costs involved (size, features, types of disinfectant and plumbing, etc.). It is unlikely this rule change will have an ongoing cost or savings as the rule changes do not affect the operation of the pool.
The head of Department of Health, Dr. Joseph Miner, has reviewed and approved this fiscal analysis.
R392. Health, Disease Control and Prevention, Environmental Services.
R392-302. Design, Construction and Operation of Public Pools.
R392-302-1. Authority and Purpose of Rule.
This rule is authorized under Sections 26-1-5, 26-1-30 (23) and 26-15-2. It establishes minimum standards for the design, construction, operation and maintenance of public pools and provides for the prevention and control of health hazards associated with public pools which are likely to affect public health .
The following definitions apply in this rule.
(1) "AED" means automated external defibrillator.
(2) "Backwash" means the process of cleaning a swimming pool filter by reversing the flow of water through the filter.
(3) "Bather Load" means the number of persons using a pool at any one time or specified period of time.
(4) "Cleansing shower" means the cleaning of the entire body surfaces with soap and water to remove any matter, including fecal matter, that may wash off into the pool while swimming.
(5) "Collection Zone" means the area of an interactive water feature where water from the feature will be collected and drained for treatment.
(6) "CPR" means Cardiopulmonary Resuscitation.
(7) "Department" means the Utah Department of Health.
(8) "Executive Director" means the Executive Director of the Utah Department of Health, or his designated representative.
(9) "Facility" means any premises, building, pool, equipment, system, and appurtenance which appertains to the operation of a public pool.
(10) "Float Tank" means a tank containing a skin-temperature solution of water and Epsom salts at a specific gravity high enough to allow the user to float supine while motionless and require a deliberate effort by the user to turn over and that is designed to provide for solitary use and sensory deprivation of the user.
(11) "Gravity Drain System" means a pool drain system wherein the drains are connected to a surge or collector tank and rather than drawing directly from the drain, the circulation pump draws from the surge or collector tank and the surface of the water contained in the tank is maintained at atmospheric pressure.
(12) "High Bather Load" means 90% or greater of the designed maximum bather load."
(13) "Hydrotherapy Pool" means a pool designed primarily for medically prescribed therapeutic use.
(14) "Illuminance Uniformity" means the ratio between the brightest illuminance falling on a surface compared to the lowest illuminance falling on a surface within an area. The value of illuminance falling on a surface is measured in foot candles.
15]) "Interactive Water Feature" means a
recirculating water feature designed, installed or used for
recreational use, in which there is direct water contact from the
feature with the public, and when not in operation, all water
drains freely so there is no ponding.
16]) "Lamp Lumens" means the quantity of light,
illuminance, produced by a lamp.
17]) "Lifeguard" means an attendant who supervises
the safety of bathers.
18]) "Living Unit" means one or more rooms or
spaces that are, or can be, occupied by an individual, group of
individuals, or a family, temporarily or permanently for
residential or overnight lodging purposes. Living units include
motel and hotel rooms, condominium units, travel trailers,
recreational vehicles, mobile homes, single family homes, and
individual units in a multiple unit housing complex.
19]) "Local Health Officer" means the health
officer of the local health department having jurisdiction, or his
20]) "Onsite Septic System" means an approved
onsite waste water system designed, constructed, and operated in
accordance with Rule 317-4.
21]) "Pool" means a man-made basin, chamber,
receptacle, tank, or tub, above ground or in-ground, which, when
filled with water, creates an artificial body of water used for
swimming, bathing, diving, recreational and therapeutic uses.
22]) "Pool Deck" means the area contiguous to the
outside of the pool curb, diving boards, diving towers and
23]) "Pool Shell" means the rigid encasing
structure of a pool that confines the pool water by resisting the
hydrostatic pressure of the pool water, resisting the pressure of
any exterior soil, and transferring the weight of the pool water
(sometimes through other supporting structures) to the soil or the
building that surrounds it.
24]) "Private Residential Pool" means a swimming
pool, spa pool or wading pool used only by an individual, family,
or living unit members and guests, but not serving any type of
multiple unit housing complex of four or more living units.
25]) "Public Pool" means a swimming pool, spa pool,
wading pool, or special purpose pool facility which is not a
private residential pool and may be above ground or in-ground.
26]) "Saturation Index" means a value determined by
application of the formula for calculating the saturation index in
Table 5, which is based on interrelation of temperature, calcium
hardness, total alkalinity and pH which indicates if the pool water
is corrosive, scale forming or neutral.
27]) "Spa Pool" means a pool which uses therapy jet
circulation, hot water, cold water, bubbles produced by air
induction, or any combination of these, to impart a massaging
effect upon a bather. Spa pools include, spas, whirlpools, hot
tubs, or hot spas.
28]) "Special Purpose Pool" means a pool with
design and operational features that provide patrons recreational,
instructional, or therapeutic activities which are different from
that associated with a pool used primarily for swimming, diving, or
29]) "Splash Pool" means the area of water located
at the terminus of a water slide or vehicle slide.
30]) "Swimming Pool" means a pool used primarily
for recreational, sporting, or instructional purposes in bathing,
swimming, or diving activities.
31]) "Surge Tank" means a tank receiving the
gravity flow from an overflow gutter and main drain or drains from
which the circulation pump takes water which is returned to the
32]) "Turnover" means the circulation of a quantity
of water equal to the pool volume through the filter and treatment
33]) "Vehicle Slide" means a recreational pool
where bathers ride vehicles, toboggans, sleds, etc., down a slide
to descend into a splash pool.
34]) "Unblockable Drain" means a drain of any size
or shape such that a representation of the torso of a 99 percentile
adult male cannot sufficiently block it to the extent that it
creates a body suction entrapment hazard.
35]) "Wading Pool" means any pool or pool area used
or designed to be used by children five years of age or younger for
wading or water play activities.
36]) "Waste Water" means discharges of pool water
resulting from pool drainage or backwash.
37]) "Water Slide" means a recreational facility
consisting of flumes upon which bathers descend into a splash
R392-302-11. Diving Areas.
(1) Where diving is permitted, the diving area design, equipment placement, and clearances must meet the minimum standards established by the USA Diving Rules and Regulations 2004, Appendix B, which are incorporated by reference.
(2) Where diving from a height of less than 3.28 feet, 1 meter, from normal water level is permitted, the diving bowl shall meet the minimum depths outlined in Section 6, Figure 1 and Table 2 of ANSI/NSPI-1, 2003, which is adopted by reference, for type VI, VII and VIII pools according to the height of the diving board above the normal water level. ANSI/NSPI pool type VI is a maximum of 26 inches, 2/3 meter, above the normal water level; type VII is a maximum of 30 inches, 3/4 meter, above the normal water level; and type VIII is a maximum of 39.37 inches, 1 meter, above the normal water level.
(3) The use of a starting platform is restricted to competitive swimming events or supervised training for competitive swimming events.
(a) If starting platforms are used for competitive swimming or training, the water depth shall be at least four feet.
(b) The operator shall either remove the starting platforms or secure them with a lockable cone-type platform safety cover when not in competitive use.
(4) Areas of a pool where diving is not
permitted must have "NO DIVING" or the international no
diving icon, or both provided in block letters at least four
inches, 10.16 centimeters, in height, as required in R392-302-[
34] (3)(a), in a contrasting color on the deck, located on
the horizontal surface of the deck or coping as close to the
water's edge as practical.
(a) Where the "NO DIVING" warnings are used, the spacing between each warning may be no greater than 25 feet, 7.62 centimeters.
(b) Where the icon alone is used on the deck as required, the operator shall also post at least one "NO DIVING" sign in plain view within the enclosure. Letters shall be at least four inches, 10.16 centimeters, in height with a stroke width of at least one-half inch.
R392-302-14. Fencing and Barriers.
(1) A fence or other barrier is required and must provide complete perimeter security of the facility, and be at least 6 feet, 1.83 meters, in height. Openings through the fence or barrier, other than entry or exit access when the access is open, may not permit a sphere greater than 4 inches, 10.16 centimeters, to pass through it at any location. Horizontal members shall be equal to or more than 45 inches, 114.3 centimeters, apart.
(a) If the local health department determines that the safety of children is not compromised, it may exempt indoor pools from the fencing requirements.
(b) The local health department may grant exceptions to the height requirements in consideration of architectural and landscaping features for pools designed for hotels, motels and apartment houses.
(2) A fence or barrier that has an entrance to the facility must be equipped with a self-closing and self-latching gate or door. Except for self-locking mechanisms, self-latching mechanisms must be installed 54 inches, 1.37 meters, above the ground and must be provided with hardware for locking the gate when the facility is not in use. A lock that is separate from the latch and a self locking latch shall be installed with the lock's operable mechanism (key hole, electronic sensor, or combination dial) between 34 inches, 86.4 centimeters, and 48 inches, 1.219 meters, above the ground. All gates for the pool enclosure shall open outward from the pool.
(3) The gate or door shall have no opening greater than 0.5 inches, 1.27 centimeters, within 18 inches, 45.7 centimeters, of the latch release mechanism.
(4) Any pool enclosure which is accessible
to the public when one or more of the pools are not being
maintained for use, shall protect those closed pools from access by
a sign meeting R392-302-[
34] (3)(a) indicating the pool is closed and by using:
(a) a safety cover which restricts access and meets the minimum ASTM standard F1346-91; or
(b) a secondary barrier that is approved by the Department; or
(c) any method approved by the Department.
R392-302-15. Depth Markings and Safety Ropes.
(1) The depth of the water must be plainly
marked at locations of maximum and minimum pool depth, and at the
points of separation between the swimming and non-swimming areas of
a pool. Pools must also be marked at intermediate 1 foot, 30.48
centimeters, increments of depth, spaced at distances which do not
exceed 25 feet, 7.62 meters. Markings must be located above the
water line or within 2 inches, 5.8 centimeters, from the coping on
the vertical wall of the pool and on the edge of the deck or walk
next to the pool with numerals at least 4 inches, 10.16
centimeters, high as required in R392-302-[
(2) A pool with both swimming and diving areas must have a floating safety rope separating the swimming and diving areas. An exception to this requirement is made for special activities, such as swimming contests or training exercises when the full unobstructed length of the pool is used.
(a) The safety rope must be securely fastened to wall anchors. Wall anchors must be of corrosion-resistant materials and must be recessed or have no projections that may be a safety hazard if the safety rope is removed.
(b) The safety rope must be marked with visible floats spaced at intervals of 7 feet, 2.13 meters or less.
(c) The rope must be at least 0.5 inches, 1.27 centimeters, in diameter, and of sufficient strength to support the loads imposed on it during normal bathing activities.
(3) A pool constructed with a change in the slope of the pool floor must have the change in slope designated by a floating safety rope and a line of demarcation on the pool floor.
(a) The floating safety rope designating a change in slope of the pool floor must be attached at the locations on the pool wall that place it directly above and parallel to the line on the bottom of the pool. The floating safety rope must meet the requirements of Subsections R392-302-15(2)(a),(b),(c).
(b) A line of demarcation on the pool floor must be marked with a contrasting dark color.
(c) The line must be at least 2 inches, 5.08 centimeters, in width.
(d) The line must be located 12 inches, 30.48 centimeters, toward the shallow end from the point of change in slope.
(4) The department may exempt a spa pool from the depth marking requirement if the spa pool owner can successfully demonstrate to the department that bather safety is not compromised by the elimination of the markings.
(1) No feature or circulation pump shall be connected to less than two outlets unless the pump is connected to a gravity drain system or the pump is connected to an unblockable drain. All pool outlets shall meet the following design criteria:
(a) The grates or covers of all submerged outlets in pools shall conform to the standards of ANSI/APSP-16 2011.
(b) The outlets must be constructed so that if one of the outlets is completely obstructed, the remaining outlets and related piping will be capable of handling 100 percent of the maximum design circulation flow.
(c) All pool outlets that are connected to a pump through a single common suction line must connect to the common suction line through pipes of equal diameter. The tee feeding to the common suction line from the outlets must be located approximately midway between outlets.
(d) An outlet system with more than one outlet connected to a pump suction line must not have any valve or other means to cut any individual outlet out of the system.
(e) At least one of the circulation outlets shall be located at the deepest point of the pool and must be piped to permit the pool to be completely and easily emptied.
(f) The center of the outlet covers or grates of multiple main drain outlets shall not be spaced more than 30 feet, 9.14 meters, apart nor spaced closer than 3 feet, 0.914 meters, apart.
(g) Multiple pumps may utilize the same outlets only if the outlets are sized to accommodate 100 percent of the total combined design flow from all pumps and only if the flow characteristics of the system meet the requirements of subsection R392-302-18(2) and (3).
(h) There must be one main drain outlet for each 30 feet, 9.14 meters, of pool width. The centers of the outlet covers or grates of any outermost main drain outlets must be located within 15 feet, 4.57 meters, of a side wall.
(i) Devices or methods used for draining pools shall prevent overcharging the sanitary sewer.
(j) No operator shall allow the use of a pool with outlet grates or covers that are broken, damaged, missing, or not securely fastened.
(2) Notwithstanding Section R392-302-3, all public pools must comply with Subsections R392-302-18(2) and (3). The pool operator shall not install, allow the installation of, or operate a pool with a drain, drain cover, or drain grate in a position or an application that conflicts with any of the following mandatory markings on the drain cover or grate under the standard required in R392-302-18(1)(a):
(a) whether the drain is for single or multiple drain use;
(b) the maximum flow through the drain cover; and
(c) whether the drain may be installed on a wall or a floor.
(3) The pool operator shall not install, allow the installation of, or operate a pool with a drain cover or drain grate unless it is over or in front of:
(a) the sump that is recommended by the drain cover or grate manufacturer;
(b) a sump specifically designed for that drain by a Registered Design Professional as defined in ANSI/APSP-16 2011; or
(c) a sump that meets the ANSI/APSP-16 2011 standard.
(4) Notwithstanding Section R392-302-3, all public pools must comply with this subsection R392-302-18(4). The pool owner or certified pool operator shall retrofit by December 19, 2009 each pool circulation system on existing pools that do not meet the requirements of subsections R392-302-18(1) through R392-302-18(1)(g) and R392-302-18(2) through (3)(c). The owner or operator shall meet the retrofit requirements of this subsection by any of the following means:
(a) Meet the requirements of R392-302-18(1)(a) and R392-302-18(2) through (3)(c) and install a safety vacuum release system which ceases operation of the pump, reverses the circulation flow, or otherwise provides a vacuum release at a suction outlet when it detects a blockage; that has been tested by an independent third party; and that conforms to ASME standard A112.19.17-2010 or ASTM standard F2387-04(2012);
(i) To ensure proper operation, the certified pool operator shall inspect and test the vacuum release system at least once a week but no less often than established by the manufacturer. The certified pool operator shall test the vacuum release system in a manner specified by the manufacturer. The certified pool operator shall log all inspections, tests and maintenance and retain the records for a minimum of two years for review by the Department and local health department upon request.
(ii) The vacuum release system shall
include a notification system that alerts patrons and the pool
operator when the system has inactivated the circulation system.
The pool operator shall submit to the local health department for
approval the design of the notification systems prior to
installation. The system shall activate a continuous clearly
audible alarm that can be heard in all areas of the pool or a
continuous visible alarm that can be seen in all areas of the pool.
A sign that meets the requirements of a "2 Inch Safety
Sign" in R392-302-[
34] (1),(2) and (3)(b) shall be posted next to the sound or
visible alarm source. The sign shall state, "DO NOT USE THE
POOL IF THIS ALARM IS ACTIVATED." and provide the phone number
of the pool operator.
(iii) No operator shall allow the use of a pool that has a single drain with a safety vacuum release system if the safety vacuum release system is not functioning properly.
(b) Install an outlet system that includes no fewer than two suction outlets separated by no less than 3 feet, 0.914 meters, on the horizontal plane as measured from the centers of the drain covers or grates or located on two different planes and connected to pipes of equal diameter. The outlet system shall meet the requirements of R392-302-18(1)(a) through R392-302-18(1)(g) and 18(2) through (3)(c);
(c) Meet the requirements of R392-302-18(1)(a) and R392-302-18(2) through (3)(c) and installing (or having an existing) gravity drain system;
(d) Install an unblockable drain that meets the requirements of R392-302-18(1)(a) and R392-302-18(2) through (3)(c); or
(e) Any other system determined by the federal Consumer Products Safety Commission to be equally effective as, or better than, the systems described in 15 USC 8003 (c)(1)(A)(ii)(I), (III), or (IV) at preventing or eliminating the risk of injury or death associated with pool drainage systems.
(1) The filter system must provide for isolation of individual filters for backwashing or other service.
(2) The filtration system must be designed to allow the pool operator to easily observe the discharge backwash water from the filter in order to determine if the filter cells are clean.
(3) A public pool must use either a rapid sand filter, hi-rate sand filter, precoat media filter, a cartridge filter or other filter types deemed equivalent by the Department. All filters must comply with the standard NSF/ANSI 50-2015.
(4) Gravity and pressure rapid sand filter requirements.
(a) Rapid sand filters must be designed for a filter rate of 3 gallons, 11.36 liters, or less, per minute per square foot, 929 square centimeters, of bed area at time of maximum head loss. The filter bed surface area must be sufficient to meet the design rate of flow required by Section R392-302-16, Table 1, for required turnover.
(b) The filter system must be provided with influent pressure, vacuum, or compound gauges to indicate the condition of the filters. Air-relief valves must be provided at or near the high point of the filter or piping system.
(c) The filter system must be designed with necessary valves and piping to permit:
(i) filtering of all pool water;
(ii) individual backwashing of filters to a sanitary sewer at a minimum rate of 15 gallons, 56.78 liters, per minute per square foot, 929 square centimeters, of filter area;
(iii) isolation of individual filters;
(iv) complete drainage of all parts of the system;
(v) necessary maintenance, operation and inspection in a convenient manner.
(d) Each pressure type filter tank must be provided with an access opening of at least a standard size 11 inch, 27.94 centimeters, by 15 inch, 38.10 centimeters, manhole with a cover.
(5) Hi-rate sand filter requirements.
(a) Hi-rate sand filters must be designed for a filter rate of less than 18 gallons, 68.14 liters, per minute per square foot, 929 square centimeters, of bed area. The filter bed area must be sufficient to meet the design rate of flow required by Section R392-302-16, Table 1, for required turnover. Minimum flow rates must be at least 13 gallons, 49.21 liters, per minute per square foot, 929 square centimeters, of bed area. The minimum flow rate requirement may be reduced to a rate of no less than 10 gallons per minute per square foot of bed area where a multiple filter system is provided, and where the system includes a valve or other means after the filters which is designed to regulate the backwash flow rate and to assure that adequate backwash flow can be achieved through each filter per the filter manufacturer's requirements.
(b) The filter tank and all components must be installed in compliance with the manufacturer's recommendations.
(c) An air-relief valve must be provided at or near the high point of the filter.
(d) The filter system must be provided with an influent pressure gauge to indicate the condition of the filter.
(6) Vacuum or pressure type precoat media filter requirements.
(a) The filtering area must be compatible with the design pump capacity as required by R392-302-16(7). The design rate of filtration may not exceed 2.0 gallons per minute per square foot, 7.57 liters per 929 square centimeters, of effective filtering surface without continuous body feed, nor greater than 2.5 gallons per minute per square foot, 9.46 liters per 929 square centimeters, with continuous body feed.
(b) Where body feed is provided, the feeder device must be accurate to within 10 percent, must be capable of continual feeding within a calibrated range, and must be adjustable from two to six parts per million. The device must feed at the design capacity of the circulation pump.
(c) Where fabric is used, filtering area must be determined on the basis of effective filtering surfaces.
(d) The filter and all component parts must be designed and constructed of materials which will withstand normal continuous use without significant deformation, deterioration, corrosion or wear which could adversely affect filter operations.
(e) If a precoat media filter is supplied with a potable water supply, then the water must be delivered through an air gap.
(f) The filter plant must be provided with influent pressure, vacuum, or compound gauges to indicate the condition of the filter. In vacuum-type filter installations where the circulating pump is rated at two horsepower or higher, an adjustable high vacuum automatic shut-off device must be provided to prevent damage to the pump. Air-relief valves must be provided at or near the high point of the filter system.
(g) A filter must be designed to facilitate cleaning by one or more of the following methods: backwashing, air-bump-assist backwashing, automatic or manual water spray, or agitation.
(h) The filter system must provide for complete and rapid draining of the filter.
(i) Diatomaceous earth filter backwash
water must discharge to the sanitary sewer system through a
separation tank. The separation tank must have a sign that meets
the requirements of a "2 Inch Safety Sign" in R392-302-[
34] (1), (2) and (3)(b) warning the user not to start up the
filter pump without first opening the air relief valve.
(j) Personal protection equipment suitable for preventing inhalation of diatomaceous earth or other filter aids must be provided.
(7) The department may waive NSF/ANSI 50-2015 standards for precoat media filters and approve site-built or custom-built vacuum precoat media filters, if the precoat media filter elements are easily accessible for cleaning by hand hosing after each filtering cycle. Site-built or custom-built vacuum precoat media filters must comply with all design requirements as specified in Subsection R392-302-20(6). Any design which provides the equivalent washing effectiveness as determined by the department may be acceptable. Where the department or the local health department determines that a potential cross-connection exits, a hose bib in the vicinity of the filter to facilitate the washing operation must be equipped with a vacuum breaker listed by the International Association of Plumbing and Mechanical Officials, IAPMO, the American Society of Sanitary Engineering, A.S.S.E., or other nationally recognized standard.
(8) Vacuum or pressure type cartridge filter requirements.
(a) Sufficient filter area must be provided to meet the design pump capacity as required by Subsection R392-302-16, Table 1.
(b) The designed rate of filtration may not exceed 0.375 gallons, 1.42 liters, per minute per square foot, 929 square centimeters, of effective filter area.
(c) The filter and all component parts must be designed and constructed of materials which will withstand normal continuous use without significant deformation, deterioration, corrosion or wear which could adversely affect filter operations. The filter element must be constructed of polyester fiber only.
(d) The filter must be fitted with influent and effluent pressure gauges, vacuum, or compound gauges to indicate the condition of the filter. In vacuum type filter installations where the circulating pump is rated at two horsepower or higher, an adjustable high vacuum automatic shut-off must be provided to prevent damage to the pump. Air-relief valves must be provided at or near the high point of the filter system.
(e) Cleaning of cartridge type filters must be accomplished in accordance with the manufacturer's recommendations.
R392-302-21. Disinfectant and Chemical Feeders.
(1) A pool must be equipped with disinfectant dosing or generating equipment which conform to the NSF/ANSI 50-2015, standards relating to mechanical chemical feeding equipment, or be deemed equivalent by the department.
(2) All chlorine dosing and generating equipment, including erosion feeders, or in-line electrolytic and brine/bath generators, shall be designed with a capacity to provide the following, depending on the intended use:
(a) Outdoor pools: 4.0 pounds of free available chlorine per day per 10,000 gallons of pool water; or
(b) Indoor pools: 2.5 pounds of free available chlorine per day per 10,000 gallons of pool water.
2]) Where oxidation-reduction potential controllers are used,
the operator shall perform supervisory water testing, calibration
checks, inspection and cleaning of sensor probes and chemical
injectors in accordance with the manufacturer's
recommendations. If specific manufacturer's recommendations are
not made, the operator shall perform inspections, calibration
checks, and cleaning of sensor probes at least weekly.
3]) Where compressed chlorine gas is used, the following
additional features must be provided:
(a) Chlorine and chlorinating equipment must be located in a secure, well-ventilated enclosure separate from other equipment systems or equipment rooms. Such enclosures may not be below ground level. If an enclosure is a room within a building, it must be provided with vents near the floor which terminate at a location out-of-doors. Enclosures must be located to prevent contamination of air inlets to any buildings and areas used by people. Forced air ventilation capable of providing at least one complete air change per minute, must be provided for enclosures.
(b) The operator shall not keep substances which are incompatible with chlorine in the chlorine enclosure.
(c) The operator shall secure chlorine cylinders to prevent them from falling over. The operator shall maintain an approved valve stem wrench on the chlorine cylinder so the supply can be shut off quickly in case of emergency. The operator shall keep valve protection hoods and cap nuts in place except when the cylinder is connected.
(d) A sign that meets the requirements of
a "4 Inch Safety Sign" in R392-302-[
34] (1), (2) and (3)(a) shall be attached to the entrance
door to chlorine gas and equipment rooms that reads, "DANGER
CHLORINE GAS" and display the United States Department of
Transportation placard and I.D. number for chlorine gas.
(e) The chlorinator must be designed so that leaking chlorine gas will be vented to the out-of-doors.
(f) The chlorinator must be a solution feed type, capable of delivering chlorine at its maximum rate without releasing chlorine gas to the atmosphere. Injector water must be furnished from the pool circulation system with necessary water pressure increases supplied by a booster pump. The booster must be interlocked with both the pool circulation pump and with a flow switch on the return line.
(g) Chlorine feed lines may not carry pressurized chlorine gas.
(h) The operator shall keep an unbreakable bottle of ammonium hydroxide, of approximately 28 percent solution in water, readily available for chlorine leak detection.
(i) A self-contained breathing apparatus approved by NIOSH for entering environments that are immediately dangerous to life or health must be available and must have a minimum capacity of fifteen minutes.
(j) The breathing apparatus must be kept in a closed cabinet located outside of the room in which the chlorinator is maintained, and must be accessible without use of a key or lock combination.
(k) The facility operator shall demonstrate to the local health department through training documentation, that all persons who operate, or handle gas chlorine equipment, including the equipment specified in Subsections R392-203-21(3)(h) and (i) are knowledgeable about safety and proper equipment handling practices to protect themselves, staff members, and the public from accidental exposure to chlorine gas.
(l) The facility operator or his designee shall immediately notify the local health department of any inadvertent escape of chlorine gas.
4]) Bactericidal agents, other than chlorine and bromine, and
their feeding apparatus may be acceptable if approved by the
department. Each bactericidal agent must be registered by the U.S.
Environmental Protection Agency for use in swimming pools.
5]) Equipment of the positive displacement type and piping
used to apply chemicals to the water must be sized, designed, and
constructed of materials which can be cleaned and maintained free
from clogging at all times. Materials used for such equipment and
piping must be resistant to the effects of the chemicals in
6]) All auxiliary chemical feed pumps must be wired
electrically to the main circulation pump so that the operation of
these pumps is dependent upon the operation of the main circulation
pump. If a chemical feed pump has an independent timer, the main
circulation pump and chemical feed pump timer must be
R392-302-22. Safety Requirements and Lifesaving Equipment.
(1) Areas of a public pool with water depth greater than six feet or a width greater than forty feet and a depth greater than four feet where a lifeguard is required under Subsection R392-302-30(2) shall provide for a minimum number of elevated lifeguard stations in accordance with Table 2. Elevated lifeguard stations shall be located to provide a clear unobstructed view of the pool bottom by lifeguards on duty.
(2) A public pool must have at least one unit of lifesaving equipment. One unit of lifesaving equipment must consist of the following: a Coast Guard-approved ring buoy with an attached rope equal in length to the maximum width of the pool plus 10 feet and a life pole or shepherd's crook type pole with blunted ends and a minimum length of 12 feet, 3.66 meters. The facility operator may substitute a rescue tube for a ring buoy where lifeguard service is provided. Additional units must be provided at the rate of one for each 2,000 square feet, 185.8 square meters, of surface area or fraction thereof. The operator of a pool that has lifeguard services shall provide at least one backboard designed with straps and head stabilization capability.
(3) A public pool must be equipped with a first aid kit which includes a minimum of the following items:
2 Units eye dressing packet;
2 Units triangular bandages;
1 CPR shield;
6 pairs disposable medical exam gloves; and
Assorted types and sizes of the following: self adhesive bandages, compresses, roller type bandages and bandage tape.
(a) The operator shall keep the first-aid kit filled, available, and ready for use.
(4) Lifesaving equipment must be mounted in readily accessible, conspicuous places around the pool deck. The operator shall maintain it in good repair and operable condition. The operator and lifeguards shall prevent the removal of lifesaving equipment or use of it for any reason other than its intended purpose.
(5) Where no lifeguard service is provided
in accordance with Subsection R392-302-30(2), a warning sign that
meets the requirements of a "4 Inch Safety Sign" in
34] (1), (2) and (3)(a) shall be posted. The sign shall
state: WARNING - NO LIFEGUARD ON DUTY. In addition, the sign shall
state in text that meets the requirements of "2 Inch Safety
Sign" in R392-302-[ 34] (1), (2) and (3)(b) "BATHERS SHOULD NOT SWIM
ALONE", and CHILDREN 14 AND UNDER SHALL NOT USE POOL WITHOUT
RESPONSIBLE ADULT SUPERVISION.
(6) Where lifeguard service is required, the facility must have a readily accessible area designated and equipped for emergency first aid care.
Safety Equipment and Signs
POOLS WITH POOLS WITH
LIFEGUARD NO LIFEGUARD
Elevated Station 1 per 2,000 None
sq. ft., 185
of pool area
Backboard 1 per facility None
Room for Emergency Care 1 per facility None
Ring Buoy with 1 per 2,000 1 per 2,000
an attached rope sq. ft., 185 sq. ft., 185
equal in length sq. meters, sq. meters,
to the maximum of pool area of pool area
width of the pool or fraction or fraction
plus 10 feet,
Rescue Tube 1 per 2,000 None
(used as a substitute sq. ft., 185
for ring buoys when sq. meters,
lifeguards are of pool area
present) or fraction
Life Pole or 1 per 2,000 1 per 2,000
Shepherds Crook sq. ft. 185, sq. ft. 185,
sq. meters, sq. meters,
of pool area of pool area
or fraction or fraction
First Aid Kit 1 per facility 1 per facility
R392-302-27. Disinfection and Quality of Water.
(1) Disinfection Process.
(a) A pool must be continuously disinfected by a product which:
(i) Is registered with the United States Environmental Protection Agency as a disinfecting process or disinfectant product for water;
(ii) Imparts a disinfectant residual which may be easily and accurately measured by a field test procedure appropriate to the disinfectant in use;
(iii) Is compatible for use with other chemicals normally used in pool water treatment;
(iv) Does not create harmful or deleterious effects on bathers if used according to manufacturer's specifications; and
(v) Does not create an undue safety hazard if handled, stored and used according to manufacturer's specifications.
(b) The concentration levels of the active disinfectant within the pool water shall be consistent with the label instructions of the disinfectant and with the minimum levels listed in Table 6 for all circumstances, bather loads, and the pH level of the water.
(i) At no time shall the concentration level of free available chlorine reach a level above ten parts per million while the facility is open to bathers.
(2) Products used to treat or condition pool water shall be used according to the product label.
(3) Testing Kits.
(a) An easy to operate pool-side disinfectant testing kit, compatible with the disinfectant in use and accurate to within 0.5 milligrams per liter, must be provided at each pool.
(b) If chlorine is the disinfectant used, it must be tested by the diethyl-p-phenylene diamine method, the leuco crystal violet method, or another test method approved by the Department.
(c) If cyanuric acid or stabilized chlorine is used, a testing kit for cyanuric acid, accurate to within 10.0 milligrams per liter must be provided.
(d) Expired test kit reagents may not be used.
(4) Chemical Quality of Water.
(a) If cyanuric acid is used to stabilize the free residual chlorine, or if one of the chlorinated isocyanurate compounds is used as the disinfecting chemical, the concentration of cyanuric acid in the water must be at least ten milligrams per liter, but may not exceed 100 milligrams per liter.
(b) The difference between the total chlorine and the free chlorine in a pool shall not be greater than 0.5 milligrams per liter. If the concentration of combined residual chlorine is greater than 0.5 milligrams per liter the operator shall breakpoint chlorinate the pool water to reduce the concentration of combined chlorine.
(c) Total dissolved solids shall not exceed 1,500 milligrams per liter over the startup total dissolved solids of the pool water.
(d) Total alkalinity must be within the range from 100 to 125 milligrams per liter for a plaster lined pool, 80 to 150 milligrams per liter for a spa pool lined with plaster, and 125 to 150 milligrams per liter for a pool lined with other approved construction materials.
(e) A calcium hardness of at least 200 milligrams per liter must be maintained.
(f) The saturation index value of the pool water must be within the range of positive 0.3 and minus 0.3. The saturation index shall be calculated in accordance with Table 5.
(5) Water Clarity and Temperature.
(a) The water must have sufficient clarity at all times that the drain grates or covers in the deepest part of the pool are readily visible. As an alternative test for clarity, a black disk, six inches in diameter, must be readily visible if placed on a white field in the deepest part of the pool.
(b) Pool water temperatures for general use should be within the range of 82 degrees Fahrenheit, 28 degrees Celsius, to 86 degrees Fahrenheit, 30 degrees Celsius.
(c) The minimum water temperature for a pool is 78 degrees Fahrenheit, 26 degrees Celsius.
(d) The local health department may grant exemption to the pool water temperature requirements for a special purpose pool including a cold plunge pool, but may not exempt maximum hot water temperatures for a spa pool.
CHEMICAL VALUES AND FORMULA FOR CALCULATING SATURATION INDEX
The formula for calculating the saturation
SI = pH + TF + CF + AF - TDSF
SI means saturation index
TF means temperature factor
CF means calcium factor
mg/l means milligrams per liter
deg F means degrees Fahrenheit
AF means alkalinity factor
TDSF means total dissolved solids factor.
Temperature Calcium Hardness Total Alkalinity
deg. F TF mg/l CF mg/l AF
32 0.0 25 1.0 25 1.4
37 0.1 50 1.3 50 1.7
46 0.2 75 1.5 75 1.9
53 0.3 100 1.6 100 2.0
60 0.4 125 1.7 125 2.1
66 0.5 150 1.8 150 2.2
76 0.6 200 1.9 200 2.3
84 0.7 250 2.0 250 2.4
94 0.8 300 2.1 300 2.5
105 0.9 400 2.2 400 2.6
128 1.0 800 2.5 800 2.9
Total Dissolved Solids
0 to 999 12.1
1000 to 1999 12.2
2000 to 2999 12.3
3000 to 3999 12.4
4000 to 4999 12.5
5000 to 5999 12.55
6000 to 6999 12.6
7000 to 7999 12.65
each additional 1000, add .05
If the SATURATION INDEX is 0, the water is chemically in
If the INDEX is a minus value, corrosive tendencies are
If the INDEX is a positive value, scale-forming tendencies
EXAMPLE: Assume the following factors:
pH 7.5; temperature 80 degrees F, 19 degrees C;
calcium hardness 235; total alkalinity 100; and total dissolved solids 999.
pH = 7.5
TF = 0.7
CF = 1.9
AF = 2.0
TDSF = 12.1
TOTAL: 7.5 + 0.7 + 1.9 + 2.0 - 12.1 = 0.0
This water is balanced.
DISINFECTANT LEVELS AND CHEMICAL PARAMETERS
POOLS SPAS SPECIAL
Stabilized Chlorine (milligrams per liter)
pH 7.2 to 7.6 2.0(1) 3.0(1) 2.0(1)
pH 7.7 to 8.0 3.0(1) 5.0(1) 3.0(1)
Non-Stabilized Chlorine (milligrams per liter)
pH 7.2 to 7.6 1.0(1) 2.0(1) 2.0(1)
pH 7.7 to 8.0 2.0(1) 3.0(1) 3.0(1)
Bromine 4.0(1) 4.0(1) 4.0(1)
(milligrams per liter)
Iodine 1.0(1) 1.0(1) 1.0(1)
(milligrams per liter)
Ultraviolet and Hydrogen 40.0(1) 40.0(1) 40.0(1)
(milligrams per liter
pH 7.2 to 7.8 7.2 to 7.8 7.2 to 7.8
Total Dissolved 1,500 1,500 1,500
(milligrams per liter)
Cyanuric Acid 10 to 100 10 to 100 10 to 100
(milligrams per liter)
Maximum Temperature 104 104 104
Calcium Hardness 200(1) 200(1) 200(1)
(milligrams per liter as calcium carbonate)
(milligrams per liter as calcium carbonate)
Plaster Pools 100 to 125 80 to 150 100 to 125
Painted or Fiberglass 125 to 150 80 to 150 125 to 150
Saturation Index Plus or Plus or Plus or
(see Table 5) Minus 0.3 Minus 0.3 Minus 0.3
Chloramines 0.5 0.5 0.5
Note (1): Minimum Value
(6) Pool Water Sampling and Testing.
(a) At the direction of the Local Health Officer, the pool operator or a representative of the local health department shall collect a pool water sample from each public pool at least once per month or at a more frequent interval as determined by the Local health Officer. A seasonal public pool during the off season and any public pool while it is temporarily closed, if the pool is closed for an interval exceeding half of that particular month, are exempt from the requirement for monthly sampling. The operator or local health department representative shall submit the pool water sample to a laboratory approved under R444-14 to perform total coliform and heterotrophic plate count testing.
(b) The operator or local health department shall have the laboratory analyze the sample for total coliform and heterotrophic plate count using methods allowed under R444-14-4.
(c) If the operator submits the sample as required by local health department, the operator shall require the laboratory to report sample results within five working days to the local health department and operator.
(d) A pool water sample fails bacteriological quality standards if it:
(i) Contains more than 200 bacteria per milliliter, as determined by the heterotrophic plate count or
(ii) Shows a positive test for presence of coliform or contains more than 1.0 coliform organisms per 100 milliliters.
(e) Not more than 1 of 5 samples may fail bacteriological quality standards. Failure of any bacteriological water quality sample shall require submission of a second sample within one lab receiving day after the sample report has been received.
R392-302-29. Supervision of Pools.
(1) Public pools must be supervised by an operator that is certified or recertified by a program of training and testing that is approved by the Utah Department of Health. The local health department may determine the appropriate numbers of pools any one certified operator may supervise using criteria based on pool compliance history, local considerations of time and distance, and the individual operator's abilities.
(2) The pool operator must keep written records of all information pertinent to the operation, maintenance and sanitation of each pool facility. Records must be available at the facility and be readily accessible. The pool operator must make records available to the department or the local health department having jurisdiction upon their request. These records must include disinfectant residual in the pool water, pH and temperature of the pool water, pool circulation rate, quantities of chemicals and filter aid used, filter head loss, filter washing schedule, cleaning and disinfecting schedule for pool decks and dressing rooms, occurrences of fecal release into the pool water or onto the pool deck, bather load, and other information required by the local health department. The pool operator must keep the records at the facility, for at least two operating seasons.
(3) The public pool owner, in consultation with the qualified operator designated in accordance with 392-302-29 (1), shall develop an operation, maintenance and sanitation plan for the pool that will assure that the pool water meets the sanitation and quality standards set forth in this rule. The plan shall be in writing and available for inspection by the local health department. At a minimum the plan shall include the frequency of measurements of pool disinfectant residuals, pH and pool water temperature that will be taken. The plan shall also specify who is responsible to take and record the measurements.
(4) If the public pool water samples required in Section R392-302-27 (5) fail bacteriological quality standards as defined in Section R392-302-27 (5), the local health department shall require the public pool owner and qualified operator to develop an acceptable plan to correct the problem. The local health department may require more frequent water samples, additional training for the qualified operator and also may require that:
(a) the pool operator measure and record the level of disinfectant residuals, pH, and pool water temperature four times a day (if oxidation reduction potential technology is used in accordance with this rule, the local health department may reduce the water testing frequency requirement) or
(b) the pool operator read flow rate gauges and record the pool circulation rate four times a day.
(5) Bather load must be limited if necessary to insure the safety of bathers and pool water quality as required in Section R392-302-27.
(6) A sign that meets the requirements of
a "2 Inch Safety Sign" in R392-302-[
34] (1), (2) and (3)(b) must be posted in the immediate
vicinity of the pool stating the location of the nearest telephone
and emergency telephone numbers which shall include 911 or other
local emergency numbers.
R392-302-30. Supervision of Bathers.
(1) Access to the pool must be prohibited when the facility is not open for use.
(2) Lifeguard service must be provided at a public pool if direct fees are charged or public funds support the operation of the pool. If a public pool is normally exempt from the requirement to provide lifeguard services, but is used for some purpose that would require lifeguard services, then lifeguard services are required during the period of that use. For other pools, lifeguard service must be provided, or signs must be clearly posted indicating that lifeguard service is not provided.
(3) The Department shall approve programs which provide training and certifications to lifeguards. These programs shall meet the standards set in Subsection R392-302-30(4)(a).
(4) A lifeguard must:
(a) Obtain training and certification in:
(i) lifeguarding by the American Red Cross or an equivalent program; and
(ii) professional level skills in CPR, AED use, and other resuscitation skills consistent with the 2010 American Heart Association Guidelines for Cardiopulmonary Resuscitation and Emergency Cardiovascular Care; and
(iii) first aid consistent with the 2010 American Heart Association Guidelines for First Aid.
(b) Be on duty at all times when the pool is open to use by bathers, except as provided in Subsection R392-302-30(2); and
(c) Have full authority to enforce all rules of safety and sanitation.
(5) A lifeguard shall not have any other duties to perform other than the supervision and safety of bathers while he or she is assigned lifeguarding duties.
(6) Where lifeguard service is required, the number of lifeguards must be sufficient to allow for continuous supervision of all bathers, and surveillance over total pool floor areas.
(7) Lifeguards must be relieved in the rotation of lifeguarding responsibilities at least every 30 minutes with a work break of at least 10 minutes every hour.
(8) The facility operator and staff are responsible for the enforcement of the following personal hygiene and behavior rules:
(a) A bather using the facility must take a cleansing shower before entering the pool enclosure. A bather leaving the pool to use the toilet must take a second cleansing shower before returning to the pool enclosure.
(b) The operator and lifeguards shall exclude any person having a communicable disease transmissible by water from using the pool. A person having any exposed sub-epidermal tissue, including open blisters, cuts, or other lesions may not use a public pool. A person who has or has had diarrhea within the last two weeks caused by an unknown source or from any communicable or fecal-borne disease may not enter any public pool.
(c) Any child under three years old, any child not toilet trained, and anyone who lacks control of defecation shall wear a water resistant swim diaper and waterproof swimwear. Swim diapers and waterproof swimwear shall have waist and leg openings fitted such that they are in contact with the waist or leg around the entire circumference.
(d) Running, boisterous play, or rough play, except supervised water sports, are prohibited.
(e) Where no lifeguard service is provided, children 14 and under shall not use a pool without responsible adult supervision. Children under the age of five shall not use a spa or hot tub.
(f) The lifeguards and operator shall ensure that diapers shall be changed only in restrooms not at poolside. The person or persons who change the diaper must wash their hands thoroughly with soap before returning to the pool. The diapered person using a swim diaper and waterproof swimwear discussed in subsection R392-302-30(7)(c) above must undergo a cleansing shower before returning to the pool.
(f) Placards that meet the requirements of
"Rule Sign" in R392-302-[
34] (1), (2) and (3)(c) and embody the above rules of
personal hygiene and behavior must be conspicuously posted in the
pool enclosure and in the dressing rooms and lifeguard rooms (where
R392-302-31. Special Purpose Pools.
Special purpose pools] must meet all applicable requirements of all
Sections of R392-302 in addition to those of this Section as they
apply to special design features and uses of [ special purpose] pools.
Special purpose pool] projects require consultation with the local health
department having jurisdiction[ in order that consideration can be given to areas where
potential problems may exist and before deviations from some of the
requirements are approved. (b) The local health officer shall require such measures as
deemed necessary to assure the health and safety of special purpose
(2) Spa Pools.]
a]) This subsection supercedes R392-302-6(5). A spa pool
shell may be a color other than white or light pastel.
b]) Spa pools shall meet the bather load requirement of
c]) A spa pool may not exceed a maximum water depth of 4
feet, 1.22 meters. The department may grant exceptions to the
maximum depth requirement for a spa pool designed for special
purposes, such as instruction, treatment, or therapy.
d]) This subsection supercedes R392-302-12(1)(f). A spa pool
may be equipped with a single entry/exit. A spa pool must be
equipped with at least one handrail for each 50 feet, 15.24 meters,
of perimeter, or portion thereof, to designate the point of entry
and exit. Points of entry and exit must be evenly spaced around the
perimeter of the spa pool and afford unobstructed entry and
e]) This subsection supercedes R392-302-12(3)(c). In a spa
pool where the bottom step serves as a bench or seat, the bottom
riser may be a maximum of 14 inches, 35.56 centimeters.
f]) This subsection supercedes R392-302-13(1). A spa pool
must have a continuous, unobstructed deck at least 3 feet, 91.44
centimeters, wide around 25 percent or more of the spa.
g]) This subsection supercedes R392-302-13(5). The department
may allow spa decks or steps made of sealed, clear-heart
h]) A pool deck may be included as part of the spa deck if
the pools are separated by a minimum of 5 feet, 1.52 meters. An
exception is allowed to the deck and pool separation requirements
if a spa pool and another pool are constructed adjacent to each
other and share a common pool sidewall which separates the two
pools. The top surface of the common pool side wall may not exceed
18 inches, 45.7 centimeters, in width and shall have markings
indicating "No Walking" or an icon that represents the
same, provided in block letters at least four inches, 10.16
centimeters, in height, as required by R392-302-[ 34] (3)(a), in a contrasting color on the horizontal surface
of the common wall. Additionally the deck space around the
remainder of the spa shall be a minimum of five feet, 1.52
i]) This subsection supersedes R392-302-15. The local health
officer may exempt a spa pool from depth marking requirements if
the spa pool owner can successfully demonstrate to the local health
officer that bather safety is not compromised by the elimination of
j]) A spa pool must have a minimum of one turnover every 30
k]) Spa pool air induction systems shall meet the
requirements of R392-302-16(12)(a) through (b). Jet or water
agitation systems shall meet the requirements of
l]) Spa pool filtration system inlets shall be wall-type
inlets and the number of inlets shall be based on a minimum of one
for each 20 feet, 6.10 meters, or fraction thereof, of pool
m]) Spa pool outlets shall meet all of the requirements of
subsections R392-302-18(1) through R392-302-18(4)(e); however, the
following exceptions apply:
i]) Multiple spa outlets shall be spaced at least three feet
apart from each other as measured from the centers of the drain
covers or grates or a third drain shall be provided and the
separation distance between individual outlets shall be at the
maximum possible spacing.
ii]) The department may exempt an acrylic or fiberglass spa
from the requirement to locate outlets at the deepest point in the
pool if the outlets are located on side walls within three inches
of the pool floor and a wet-vacuum is available on site to remove
any water left in the pool after draining.
n]) A spa pool must have a minimum number of surface
skimmers based on one skimmer for each 100 square feet, 9.29 square
meters of surface area.
o]) A spa pool must be equipped with an oxidation reduction
potential controller which monitors chemical demands, including pH
and disinfectant demands, and regulates the amount of chemicals fed
into the pool circulation system. A spa pool constructed and
approved prior to September 16, 1996 is exempt from this
requirement if it is able to meet bacteriological quality as
required in Subsection R392-302-27 (5)(e).
p]) A spa pool is exempt from the Section R392-302-22,
except for Section R392-302-22(3).
q]) The maximum water temperature for a spa pool is 104
degrees Fahrenheit, 40 degrees Celsius.
r]) A spa pool shall meet the total alkalinity requirements
of R392-302-27 (3)(d).
s]) A spa pool must have a sign that meets the requirements
of a "Rule Sign" in R392-302-[ 34] (1),(2) and (3)(c) which contains the following
i]) The word "caution" centered at the top of the
ii]) Elderly persons and those suffering from heart disease,
diabetes or high blood pressure should consult a physician before
using the spa pool.
iii]) Persons suffering from a communicable disease
transmissible via water may not use the spa pool. Persons using
prescription medications should consult a physician before using
iv]) Individuals under the influence of alcohol or other
impairing chemical substances should not use the spa pool.
v]) Bathers should not use the spa pool alone.
vi]) Pregnant women should not use the spa pool without
consulting their physicians.
vii]) Persons should not spend more than 15 minutes in the spa
in any one session.
viii]) Children under the age of 14 must be accompanied and
supervised by at least one responsible adult over the age of 18
years, when lifeguards are not on duty.
ix]) Children under the age of five years are prohibited from
bathing in a spa or hot tub.
x]) Running or engaging in unsafe activities or horseplay in
or around the spa pool is prohibited.
t]) Water jets and air induction ports on spa pools must be
controlled by an automatic timer which limits the duration of their
use to 15 minutes per each cycle of operation. The operator shall
mount the timer switch in a location which requires the bather to
exit the spa before the timer can be reset for another 15 minute
cycle or part thereof.
(3) Wading Pools.]
a]) Wading pools shall be separated from other pools. Wading
pools may not share common circulation, filtration, or chemical
treatment systems, or walls.
b]) A wading pool may not exceed a maximum water depth of 2
feet, 60.96 centimeters.
c]) The deck of a wading pool may be included as part of
adjacent pool decks.
d]) A wading pool must have a minimum of one turnover per
hour and have a separate circulation system.
e]) A wading pool that utilizes wall inlets shall have a
minimum of two equally spaced inlets around its perimeter at a
minimum of one in each 20 feet, 6.10 meters, or fraction
f]) A wading pool shall have drainage to waste through a
quick opening valve to facilitate emptying the wading pool should
accidental bowel discharge or other contamination occur.
(4) Hydrotherapy Pools.]
a]) A hydrotherapy pool shall at all times comply with
R392-302-27 Disinfection and Quality of Water, R392-302-28 Cleaning
of Pools and R392-302-29 Supervision of Pools unless it is drained
cleaned, and sanitized after each individual use.
b]) A hydrotherapy pool is exempt from all other requirements
of R392-302, only if use of the hydrotherapy pool is restricted to
therapeutic uses and is under the continuous and direct supervision
of licensed medical or physiotherapy personnel.
c]) Local health departments may enter and examine the use of
hydrotherapy pools to respond to complaints, to assure that use of
the pool is being properly supervised, to examine records of
testing and sampling, and to take samples to assure that water
quality and cleanliness are maintained.
d]) A local health officer may grant an exception to section
R392-302-31(4)(a) if the operator of the hydrotherapy pool can
demonstrate that the exception will not compromise pool sanitation
or the health or safety of users.
(5) Water Slides.]
a]) Slide Flumes.
i]) The flumes within enclosed slides must be designed to
prevent accumulation of hazardous concentrations of toxic chemical
ii]) All curves, turns, and tunnels within the path of a slide
flume must be designed so that body contact with the flume or
tunnel does not present an injury hazard. The slide flume must be
banked to keep the slider's body safely inside the flume.
iii]) The flume must be free of hazards including joints and
mechanical attachments separations, splinters, holes, cracks, or
iv]) Wall thickness of flumes must be thick enough so that the
continuous and combined action of hydrostatic, dynamic, and static
loads and normal environmental deterioration will not cause
structural failures which could result in injury. The facility
operator or owner shall insure that repairs or patchwork maintains
original designed levels of safety and structural integrity. The
facility operator or owner shall insure that repairs or patchwork
is performed in accordance with manufacturer's guidelines.
v]) Multiple-flume slides must have parallel exits or be
constructed, so that the projected path of their centerlines do not
intersect within a distance of less than 8 feet, 2.44 meters,
beyond the point of forward momentum of the heaviest bather
permitted by the engineered design.
vi]) A slide flume exit must provide safe entry into the
splash pool. Design features for safe entry include a water backup,
and a deceleration distance adequate to reduce the slider's
exit velocity to a safe speed. Other methods may be acceptable if
safe exiting from the slide flume is demonstrated to the
b]) Flume Clearance Distances.
i]) A distance of at least 4 feet, 1.22 meters, must be
provided between the side of a slide flume exit and a splash pool
ii]) The distance between nearest sides of adjacent slide
flume exits must be at least 6 feet, 1.83 meters.
iii]) A distance between a slide flume exit and the opposite
end of the splash pool, excluding steps, must be at least 20 feet,
iv]) The distance between the side of the vehicle flume exit
and the pool side wall must be at least 6 feet, 1.83 meters.
v]) The distance between nearest sides of adjacent vehicle
slide flume exits must be at least 8 feet, 2.44 meters.
vi]) The distance between a vehicle slide flume exit and the
opposite end of the splash pool, excluding steps, must be long
enough to provide clear, unobstructed travel for at least 8 feet,
2.44 meters, beyond the point of forward momentum of the heaviest
bather permitted by the engineered design.
c]) Splash Pool Dimensions.
i]) The depth of a water slide splash pool at the end of a
horizontally oriented slide flume exit must be at least 3 feet,
9.14 centimeters, but may be required to be deeper if the pool
design incorporates special features that may increase risks to
bathers as determined by the department.
ii]) The depth must be maintained in front of the flume for a
distance of at least 20 feet, 6.10 meters, from which point the
splash pool floor may have a constant slope upward. Slopes may not
be designed or constructed steeper than a 1 to 10 ratio.
iii]) The operating water depth of a vehicle slide splash pool,
at the flume exit, must be a minimum of 3 feet 6 inches, 1.07
meters. This depth must be maintained to the point at which forward
travel of the vehicle ends. From the point at which forward travel
ends, the floor may have a constant upward slope to the pool exit
at a ratio not to exceed 1 to 10.
iv]) The department may waive minimum depth and distance
requirements for a splash pool and approve a special exit system if
the designer can demonstrate to the department that safe exit from
the flume into the splash pool can be assured.
v]) A travel path with a minimum width of 4 feet, 1.22
meters, must be provided between the splash pool deck and the top
of the flume.
d]) General Water Slide Requirements.
i]) Stairways serving a slide may not retain standing water.
Stairways must have non-slip surfaces and shall conform to the
requirements of applicable building codes.
ii]) Vehicles, including toboggans, sleds, inflatable tubes,
and mats must be designed and manufactured of materials which will
safeguard the safety of riders.
iii]) Water slides shall meet the bather load requirements of
e]) Water Slide Circulation Systems.
i]) Splash pool overflow reservoirs must have sufficient
volume to contain at least two minutes of flow from the splash pool
overflow. Splash pool overflow reservoirs must have enough water to
insure that the splash pool will maintain a constant water
ii]) The circulation and filtration equipment of a special
purpose pool must be sized to turn over the entire system's
water at least once every hour.
iii]) Splash pool overflow reservoirs must circulate water
through the water treatment system and return when flume supply
service pumps are turned off.
iv]) Flume pumps and motors must be sized, as specified by the
flume manufacturer, and must meet all NSF/ANSI 50-2015, Section 6.
Centrifugal Pumps, standards for pool pumps.
v]) Flume supply service pumps must have check valves on all
vi]) The splash pool and the splash pool overflow reservoir
must be designed to prohibit bather entrapment as water flows from
the splash pool to the overflow reservoir.
vii]) Perimeter overflow gutter systems must meet the
requirements of Section R392-302-19, except that gutters are not
required directly under slide flumes or along the weirs which
separate splash pools and splash pool overflow reservoirs.
viii]) Pump reservoir areas must be accessible for cleaning and
f]) Slide Signs.
i]) Signs that meet the requirements in R392-302-[ 34] (1), (2) and (3)(c) and reflecting the slide
manufacturer's recommendations must be mounted adjacent to the
entrance to a water slide and at other appropriate areas in
accordance with R392-302-[ 34] (1). The heading of the signs shall be, "SLIDE
INSTRUCTIONS, WARNINGS, AND REQUIREMENTS". The body of the
signs shall state at least the following:
A]) Instructions including:
I]) proper riding position,
II]) expected rider conduct,
III]) dispatch procedures,
IV]) exiting procedures, and
V]) obeying slide attendants or lifeguards.
B]) Warnings to include:
I]) slide characteristics such as speed, and
II]) depth of water in splash zone.
C]) Requirements which include that riders being free of
medical conditions identified by the manufacturer such as
pregnancy, heart conditions, back conditions, or musculoskeletal
(6) Interactive Water Feature Requirements.]
a]) All parts of the interactive water feature shall be
designed, constructed, maintained, and operated so there are no
slip, fall, or other safety hazards, and shall meet the standards
of the State Construction Code Title 15a, State Construction and
Fire Codes Act.
b]) Interactive water feature nozzles that spray from the
ground level shall be flush with the ground, with openings no
greater than one-half inch in diameter. Spray devices that extend
above ground level shall be clearly visible.
c]) Areas adjacent to the water feature collection zones
shall be sloped away at a minimum of two percent from the
interactive water feature to deck drains or other approved surface
water disposal systems. A continuous deck at least 3 feet, 0.91
meters, wide as measured from the edge of the collection zones must
extend completely around the interactive water feature.
d]) Water discharged from all interactive water feature
fountain or spray features shall freely drain by gravity flow
through a main drain fitting to a below grade sump or collection
system which discharges to a collector tank.
e]) All interactive water feature foggers and misters that
produce finely atomized mists shall be supplied directly from a
potable water source and not from the underground reservoir.
f]) The interactive water feature shall have an automated
oxidation reduction potential (ORP) and pH controller installed and
in operation whenever the feature is open for use. The controller
shall be capable of maintaining disinfection and pH levels within
the requirements for special purpose pools listed in Table 6. In
addition, an approved secondary disinfection system the meets the
requirements of in R392-302-[ 33] (4)(c) through (4)(f)(iii) shall be installed and in
operation whenever the feature is open for use.
g]) A sign that meets the requirement R392-302-[ 34] (1), (2) and (3)(c) stating:
i]) The word "CAUTION" centered at the top of the
ii]) No running on or around the interactive water
iii]) Children under the age of 12 must have adult
iv]) No food, drink, glass or pets are allowed on or around
the interactive water feature.
v]) For the health of all users restrooms shall be used for
the changing of diapers.
h]) If the interactive water feature is operated at night,
five foot-candles of light shall be provided in the all areas of
the water feature. Lighting shall be installed in accordance with
manufacturer's specifications and approved for such use by UL
i]) The interactive water feature filter system shall be
capable of filtering and treating the entire water volume of the
water feature within 30 minutes.
ii]) The interactive water feature filter system shall draft
from the collector tank and return filtered and treated water to
the tank via a minimum of 4 equally spaced inlet fittings. Inlet
spacing shall also meet the requirements of section
iii]) The interactive water feature circulation system shall be
on a separate loop and not directly interconnected with the
interactive water feature pump.
iv]) The suction intake of the interactive water feature pump
in the underground reservoir shall be located adjacent to the
circulation return line and shall be located to maximize uniform
circulation of the tank.
v]) An automated water level controller shall be provided for
the interactive water feature, and the drinking water line that
supplies the feature shall meet the requirements of R392-302-4.
vi]) The water velocity through the feature nozzles of the
interactive water features shall meet manufacturer's
specifications and shall not exceed 20 feet per second.
vii]) The minimum size of the interactive water feature sump or
collector tank shall be equal to the volume of 3 minutes of the
combined flow of all feature pumps and the filter pump. Access lids
or doors shall be provided to the sump and collector tank. The lids
or doors shall be sized to allow easy maintenance and shall provide
security from unauthorized access. Stairs or a ladder shall be
provided as needed to ensure safe entry into the tank for cleaning
viii]) The suction intake from the interactive water feature
circulation pump shall be located in the lowest portion of the
ix]) A means of vacuuming and completely draining the
interactive water feature tank shall be provided.
j]) An interactive water feature is exempt from:
i]) The wall requirement of section R392-302-10;
ii]) The ladder, recessed step, stair, and handrail
requirements of section R392-302-12;
iii]) The fencing and access barrier requirements of section
iv]) The outlet requirements of section R392-302-18 except any
submerged outlet that may create an entrapment hazard to users of
the feature shall meet the requirements of R392-302-18(1)(a);
v]) The overflow gutter and skimming device requirements of
vi]) The safety and lifesaving requirements of section
R392-302-22, except that an interactive water feature shall be
equipped with a first aid kit as required by subsection
vii]) The restroom and shower facility requirements of section
R392-302-25 as long as toilets, lavatories and changing tables are
available within 150 feet;
viii]) The pool water clarity and temperature requirements of
ix]) The diving area requirement of R392-302-11 except
R392-302-11(4)(a) and (b) may be required by the Local Health
Officer if the Local Health Officer determines that a diving risk
x]) The depth marking and safety rope requirements of
xi]) The underwater lighting requirements of
R392-302-23(1),(2), and (3);
xii]) The supervision of bathers requirements of
xiii]) The bather load requirements of R392-302-7; and
xiv]) The pool color requirements of R392-302-6(5).
k]) All interactive water features shall be constructed with
a collection zone that meets the requirements of R392-302-6. Vinyl
liners that are not bonded to a collection zone surface are
prohibited. A vinyl liner that is bonded to a collection zone shall
have at least a 60 millimeter thickness. Sand, clay, or earth
collection zones are prohibited.
i]) The collection zone material of an interactive water
feature must withstand the stresses associated with the normal uses
of the interactive water feature and regular maintenance. The
collection zone structure and associated tanks shall withstand,
without any damage to the structure, the stresses of complete
emptying of the interactive water feature and associated tanks
without shoring or additional support.
ii]) The collection zone of an interactive water feature must
be designed and constructed in a manner that provides a smooth,
easily cleanable, non-abrasive, and slip resistant surface. The
collection zone surfaces must be free of cracks or open joints with
the exception of structural expansion joints or openings that allow
water to drain to the collector tank. Openings that drain to the
collector tank shall not pass a one-half inch sphere. The owner of
a non-cementitious interactive water feature shall submit
documentation with the plans required in R392-302-8 that the
surface material has been tested and passed by an American National
Standards Institute (ANSI) accredited testing facility using one of
the following standards that is appropriate to the material
A]) for pools built with prefabricated pool sections or pool
members, the International Cast Products Association (ICPA)
standard ANSI/ICPA SS-1-2001; or
B]) a standard that has been approved by the Department
based on whether the standard is applicable to the surface and
whether it determines compliance with the requirements of Section
32]. Advisory Committee.
(1) An advisory committee to the Department regarding regulation of public pools is hereby authorized.
(2) The advisory committee shall be appointed by the Executive Director. Representatives from local health departments, pool engineering, construction or maintenance companies and pool owners may be represented on the committee.
(3) Consistent with R380-1, the Executive Director may seek the advice of the advisory committee regarding interpretation of this rule, the granting of exemptions and related matters.
33]. Cryptosporidiosis Watches and Warnings.
(1) The Executive Director or local health officer may issue cryptosporidiosis watches or cryptosporidiosis warnings as methods of intervention for likely or indicated outbreaks of cryptosporidiosis. The Executive Director or local health officer may issue a cryptosporidiosis watch if there is a heightened likelihood of a cryptosporidiosis outbreak. The Executive Director or local health officer may issue a cryptosporidiosis warning if there have been reports of cryptosporidiosis above the background level reported for the disease. The Executive Director or local health officer shall include the geographic area and pool type covered in the warning and may restrict certain persons from using public pools.
(2) If a cryptosporidiosis watch or a cryptosporidiosis warning has been issued, the operator of any public pool shall post a notice sign meeting at a minimum the ANSI Z535.2-2011 requirements for NOTICE signs with a 10-foot viewing distance and approved by the local health officer. An Adobe Acrobat .pdf version of the sign that meets the requirements of this section shall be made available from the Department or the local health department. The notice sign shall be placed so that all patrons are alerted to the cryptosporidium-targeted requirements prior to deciding whether to use the swimming pool. The sign shall be at least 17 inches, 43 centimeters, wide by 11 inches, 28 centimeters, high.
(a) Centered immediately below the blue panel shall appear the words "CRYPTO DISEASE PREVENTION" in capital letters.
(b) The body of the notice sign shall be in upper case letters at least 1.0 centimeters high and include the following four bulleted statements in black letters:
-All with diarrhea in the past 2 weeks shall not use the pool.
-All users must shower with soap to remove all fecal material prior to pool entry and after using the toilet or a diaper change.
-All less than 3 yrs or who wear diapers must wear a swim diaper and waterproof swimwear. Diapers may only be changed in restrooms or changing stations.
-Keep pool water out of your mouth.
(3) If a cryptosporidium warning has been issued, each operator of a public pool subject to the warning shall, at a minimum, implement the following cryptosporidium counter measures:
(a) maintain the disinfectant concentration within the range between two mg/l (four mg/l for bromine) and the concentration listed on the product's Environmental Protection Agency mandated label as the maximum reentry concentration, but in no case more than five mg/l (10 mg/l for bromine);
(b) maintain the pH between 7.2 and 7.5; and
(c) maintain the cyanuric acid level that meets the requirement of R392-302-27(3), except the maximum level shall be reduced to 30 mg/l.
(4)(a) If a cryptosporidium warning has
been issued, in addition to the requirements listed in R392-302-[
33] (3), the owner or operator of a public pool shall
implement any additional cryptosporidium countermeasures listed in
subsection below sufficient to achieve at least a 99.9 percent
destruction or removal of cryptosporidium oocysts twice weekly,
except as provided in R392-302-[ 33] (4)(b).
(b) Hyperchlorination using sodium hypochlorite or calcium hypochlorite to achieve a concentration multiplied by time (CT) value of 15,300 mg/l minutes. Table 7 lists examples of chlorine concentrations and time periods that may be used to achieve the required CT value. The operator shall not allow anyone to use the pool if the chlorine concentration exceeds the Environmental Protection Agency maximum reentry concentration listed on the product's label, but in no case if the concentration exceeds five mg/l. The operator of any public pool not required to have a lifeguard by R392-302-30 (2) shall hyperchlorinate at least once weekly.
(c) A full flow ultraviolet treatment system that meets the requirements of standard NSF/ANSI 50-2015 for ultraviolet light process equipment. The owner or operator shall ensure that the system is installed and operated according to the manufacturer's recommendations. The owner or operator shall obtain from the manufacturer of the system documentation of third-party challenge testing that the system can achieve a single pass 99.9 percent inactivation of cryptosporidium or the bacteriophage MS2 at the pool design flow rate and during normal operating conditions. The owner or operator shall maintain and make available for inspection the manufacturer's documentation.
(d) An ozone treatment system that achieves a CT value of 7.4 and a flow-through rate at least four times the volume of the pool every three and a half days. The system shall meet the requirements of standard NSF/ANSI 50-2015 for ozone process equipment. The owner or operator shall ensure that the system is installed and operated according to the manufacturer's recommendations.
(e) A cryptosporidium oocyst-targeted filter system installed and operated according to the manufacturer's recommendations. The filter shall meet the requirements of R392-302-20. The owner or operator shall obtain from the manufacturer of the system documentation of third-party challenge testing that the system can achieve a single pass 99 percent reduction of particles in the range of 4 to 6 microns or cryptosporidium oocysts at the pool design flow rate and normal operating conditions. The owner or operator shall maintain and make available for inspection the manufacturer's documentation.
(f) A system approved by the local health officer. The health officer's approval of a system for use as an alternative shall be based on the system's documented ability to:
(i) achieve cryptosporidium removal or
inactivation to a level at least equivalent to the requirements in
(ii) assure safety for swimmers and pool operators; and
(iii) comply with all other applicable rules and federal regulations.
Chlorine Concentration and Contact Time to Achieve CT = 15,300
Chlorine Concentration Contact Time
1.0 mg/l 15,300 minutes (255 hours)
10 mg/l 1,530 minutes (25.5 hours)
20 mg/l 765 minutes (12.75 hours)
(5) If the Executive Director or local health officer issues a restriction on the use of public pools by certain persons as part of the cryptosporidium warning the operator shall restrict persons within that segment of the population from using the facility.
(6) If the Executive Director or local health officer determines that a pool is a cryptosporidiosis threat to public health, he may order the pool to close. The owner or operator of the pool may not reopen until the person issuing the order has rescinded it.
(1) Signs required in R392-302 shall be placed to alert and inform patrons in enough time that the patrons may take appropriate actions.
(2) Signs shall be written in a lettering style, stroke width, spacing, and contrast with the background such that the sign is clearly visible.
(3) As required in different subsections of this rule, sign lettering shall meet one or more, if stated, of the following minimum size standards:
(a) "4 Inch Safety Sign" shall be written in all capital letters that are at least four inches, 10.2 centimeters in height.
(b) "2 Inch Safety Sign" shall be written in all capital letters that are at least two inches, 5.1 centimeters, in height.
(c) "Rule Signs" shall be
written with any required signal word, warning or caution, as the
sign heading in letters at least two inches, 5.1 centimeters, in
height and the body or bulleted rules in letters at least [
1.5] inches, [ 3.8] centimeters, in height.
(i) If the sign can only be viewed from more than a distance of ten feet, 3.048 meters, the letter height shall be larger in the same proportion as the required viewing distance is to ten feet, 3.048 meters.
(ii) The Local Health Officer may approve
smaller letter sizes than those required in R392-302-[
34](3)(c) if the sign will always be viewed from less than a
ten foot, 3.048 meters, distance and if the Local Health Officer
agrees that the sign meets the requirements of R392-302-[ 34](1) and (2).
KEY: pools, spas, swimming, water
Date of Enactment or Last Substantive Amendment: [
June 1, 2017]
Notice of Continuation: November 7, 2016
Authorizing, and Implemented or Interpreted Law: 26-1-5; 26-1-30; 26-15-2
More information about a Notice of Proposed Rule is available online.
The Portable Document Format (PDF) version of the Bulletin is the official version. The PDF version of this issue is available at https://rules.utah.gov/publicat/bull_pdf/2018/b20180215.pdf. The HTML edition of the Bulletin is a convenience copy. Any discrepancy between the PDF version and HTML version is resolved in favor of the PDF version.
Text to be deleted is struck through and surrounded by brackets ([
example]). Text to be added is underlined (). Older browsers may not depict some or any of these attributes on the screen or when the document is printed.
For questions regarding the content or application of this rule, please contact Chris Nelson at the above address, by phone at 801-538-6739, by FAX at , or by Internet E-mail at email@example.com. For questions about the rulemaking process, please contact the Office of Administrative Rules.