Utah Administrative Code
The Utah Administrative Code is the body of all effective administrative rules as compiled and organized by the Division of Administrative Rules (see Subsection 63G-3-102(5); see also Sections 63G-3-701 and 702).
NOTE: For a list of rules that have been made effective since October 1, 2019, please see the codification segue page.
NOTE TO RULEFILING AGENCIES: Use the RTF version for submitting rule changes.
R311. Environmental Quality, Environmental Response and Remediation.
Rule R311-203. Underground Storage Tanks: Technical Standards.
As in effect on October 1, 2019
Table of Contents
- R311-203-1. Definitions.
- R311-203-2. Notification.
- R311-203-3. New Installations, Permits.
- R311-203-4. Underground Storage Tank Registration Fee.
- R311-203-5. UST Testing Requirements.
- R311-203-6. Secondary Containment and Under-Dispenser Containment.
- R311-203-7. Operator Inspections.
- R311-203-8. Unattended Facilities.
- Date of Enactment or Last Substantive Amendment
- Notice of Continuation
- Authorizing, Implemented, or Interpreted Law
Definitions are found in Rule R311-200.
(a) The owner or operator of an underground storage tank shall notify the Director whenever:
(1) new USTs are brought into use;
(2) the owner or operator changes;
(3) changes are made to the tank or piping system; and
(4) release detection, corrosion protection, or spill or overfill prevention systems are installed, changed or upgraded.
(b) All notifications shall be submitted on the current approved notification form.
(c) Notifications submitted to meet the requirements of R311-203-2(a)(1) through (4) shall be submitted within 30 days of the completion of the work or the change of ownership.
(d) To satisfy the requirement of Subsection 19-6-407(1)(c) the certified installer shall:
(1) complete the appropriate section of the notification form to be submitted by the owner or operator, and ensure that the notification form is submitted by the owner or operator within 30 days of completion of the installation; or
(2) provide separate notification to the Director within 60 days of the completion of the installation.
(a) Certified UST installers shall notify the Director at least 10 days, or another time period approved by the Director, before commencing any of the following activities:
(1) the installation of a full UST system or tank only;
(2) the installation of underground product piping for one or more tanks at a facility, separate from the installation of one or more tanks at a facility;
(3) the internal lining of a previously-existing tank;
(4) the installation of a cathodic protection system on one or more previously-existing tanks at a facility;
(5) the installation of a bladder in a tank;
(6) any retro-fit, replacement, or installation that requires the cutting of a manway into the tank;
(7) the installation of a spill prevention or overfill prevention device;
(8) the installation of a leak detection monitoring system; and
(9) the installation of a containment sump or under-dispenser containment.
(b) The UST installation company shall submit to the Director an UST installation permit fee of $200 when any of the activities listed in R311-203-3(a)(1) through (6) is performed on an UST system that has not qualified for a certificate of compliance before the commencement of the work.
(c) The fees assessed under 19-6-411(2)(a)(i) shall be determined based on the number of full UST installations performed by the installation company in the 12 months previous to the fee due date. Installations for which the fee assessed under 19-6-411(2)(a)(ii) and R311-203-3(c) is charged shall count toward the total installations for the 12-month period.
(d) For the purposes of Subsections 19-6-411(2)(a)(ii), 19-6-407(1)(c), and R311-203-2(d), an installation shall be considered complete when:
(1) in the case of installation of a new UST system, tank only, or product piping only, the new installation first holds a regulated substance; or
(2) in the case of installation of the components listed in Subsections R311-203-3(a)(3) through (a)(6), the new installation is functional and the UST holds a regulated substance and is operational.
(e) If, before completion of an installation for which an UST installation permit fee is required, the owner or operator decides to install additional UST system components, the installer shall notify the Director of the change. When additions are made, the UST installation permit fee shall not be increased unless the original UST installation permit fee would have been higher had the addition been considered at the time the original fee was determined.
(f) The number of UST installation companies performing work on a particular installation shall not be a factor in determining the UST installation permit fee for that installation. However, each installation company shall identify itself at the time the UST installation permit fee is paid.
(g) When a new UST system, tank only, product piping only, or new cathodic protection system is installed, the owner or operator shall submit to the Director an as-built drawing, to scale, that meets the requirements of R311-200-1(b)(2).
(a) Registration fees shall be assessed by the Department against all tanks which are not permanently closed for the entire fiscal year, and shall be billed per facility.
(b) Registration fees shall be due on July 1 of the fiscal year for which the assessment is made, or, for underground storage tanks brought into use after the beginning of the fiscal year, underground storage tank registration fees shall be due when the tanks are brought into use, as a requirement for receiving a certificate of compliance.
(c) The Director may waive all or part of the penalty assessed under Subsection 19-6-408(5) if no fuel has been dispensed from the tank on or after July 1, 1991 and if the tank has been properly closed according to Rules R311-204 and R311-205, or in other circumstances as approved by the Director.
(d) The Director shall issue a certificate of registration to owners or operators for individual underground storage tanks at a facility if:
(1) the tanks are in use or are temporarily closed according to 40 CFR Part 280 Subpart G; and,
(2) the underground storage tank registration fee has been paid.
(e) Pursuant to 19-6-408(5)(c), all past due registration fees, late payment penalties and interest must be paid before the Director may issue or re-issue a certificate of compliance regardless of whether there is a new owner or operator at the facility. However, the Director may decline active collection of past due registration fees, late payment penalties and interest if a certificate of compliance is not issued and the new owner or new operator properly closes the underground storage tanks within one year of becoming the new owner or operator of the facility.
(f) An underground storage tank will be assessed the higher registration fee established under Section 63J-1-504 if it is found to be out of significant operational compliance with leak prevention or leak detection requirements during an inspection, and remains out of compliance for six months or greater following the initial inspection. The higher registration fee shall be due July 1 following the documented six-month period of non-compliance. A tank will be out of significant operational compliance if it fails to meet any of the significant operational compliance measures stated in the EPA compliance measures matrices incorporated by Subsection R311-206-10(b)(1).
(g) When the Director is notified of the existence of a previously un-registered regulated UST, the Director shall assess the registration fee for the current fiscal year. If the UST is properly permanently closed within 90 days of the notification of the existence of the UST, the Director may decline active collection of past-due registration fees, late payment penalties, and interest for previous fiscal years.
(a) Tank tightness testing. The testing method must be able to test the UST system at the maximum level that could contain regulated substances. Tanks with overfill prevention devices that prevent product from entering the upper portion of the tank may be tested at the maximum level allowed by the overfill device.
(b) Spill prevention equipment. An individual who conducts a test of spill prevention equipment to meet the requirements of 40 CFR 280.35(a)(1)(ii) shall report the test results using:
(1) the form "Utah Spill Prevention Test", or
(2) the form "Appendix C-3 Spill Bucket Integrity Testing Hydrostatic Test Method Single and Double-Walled Vacuum Test Method", found in PEI RP1200, "Recommended Practices for the Testing and Verification of Spill, Overfill, Leak Detection and Secondary Containment Equipment at UST Facilities", or
(3) another form approved by the Director.
(c) Containment sump testing. An individual who conducts a test of a containment sump used for interstitial monitoring to meet the requirements of 40 CFR 280.35(a)(1)(ii) or a test of a piping containment sump or under-dispenser containment to meet the requirements of R311-206-11 shall report the test results using:
(1) the form "Utah Containment Sump Test", or
(2) the form "Appendix C-4 Containment Sump Integrity Testing Hydrostatic Testing Method", found in PEI RP1200, or
(3) another form approved by the Director.
(d) When a sump sensor is used as an automatic line leak detector, the secondary containment sump shall be tested for tightness annually according to the manufacturer's guidelines or standards, or by another method approved by the Director. The sensor shall be located as close as is practicable to the lowest portion of the sump.
(e) Cathodic protection testing. Cathodic protection tests shall meet the inspection criteria outlined in 40 CFR 280.31(b), or other criteria approved by the Director. The tester who performs the test shall provide the following information: location of at least three test points per tank, location of one remote test point for galvanic systems, test results in volts or millivolts, pass/fail determination for each tank, line, flex connector, or other UST system component tested, the criteria by which the pass/fail determination is made, and a site plat showing locations of test points. A re-test of any cathodic protection system is required within six months of any below-grade work that may harm the integrity of the system.
(f) UST testers performing tank and line tightness testing shall include the following as part of the test report: pass/fail determination for each tank or line tested, the measured leak rate, the test duration, the product level for tank tests, the pressure used for pressure tests, the type of test, and the test equipment used.
(a) Secondary containment for tanks and piping.
(1) To meet the requirements of Section 42 USC 6991b(i) of the Solid Waste Disposal Act, all tanks and product piping that are installed as part of an underground storage tank system after October 1, 2008 and before January 1, 2017 shall have secondary containment if the installation is located 1000 feet or less from an existing community water system or an existing potable drinking water well.
(2) The secondary containment installed under Subsection (a) shall meet the requirements of 40 CFR 280.42(b), and shall be monitored monthly for releases from the tank and piping. Monthly monitoring shall meet the requirements of 40 CFR 280.43(g).
(3) Containment sumps for piping that is installed under Subsection (a) shall be required:
(A) at the submersible pump or other location where the piping connects to the tank;
(B) where the piping connects to a dispenser, or otherwise goes above-ground; and
(C) where double-walled piping that is required under Subsection (a) connects with existing piping.
(4) Containment sumps for piping that is installed under Subsection (a) shall:
(A) contain submersible pumps, check valves, unburied risers, flexible connectors, and other transitional components that connect the piping to the tank, dispenser, or existing piping; and
(B) meet the requirements of Subsections (b)(2)(A) through (C).
(5) In the case of a replacement of tank or piping, only the portion of the UST system being replaced shall be subject to the requirements of Subsection (a). If less than 100 percent of the piping from a tank to a dispenser is replaced, the requirements of Subsection (a) shall apply to all new product piping that is installed. The closure requirements of R311-205 shall apply to all product piping that is taken out of service. When new piping is connected to existing piping that is not taken out of service, the connection between the new and existing piping shall be secondarily contained, and shall be monitored for releases according to 40 CFR 280.43(g).
(6) The requirements of Subsection (a) shall not apply to:
(A) piping that meets the requirements for "safe suction" piping in 40 CFR 280.41(b)(2)(i) through (v), or
(B) piping that connects two or more tanks to create a siphon system.
(7) The requirements of Subsection (a) shall apply to emergency generator USTs installed after October 1, 2008.
(b) Under-dispenser containment.
(1) To meet the requirements of Section 42 USC 6991b(i) of the Solid Waste Disposal Act, all new motor fuel dispenser systems installed after October 1, 2008 and before January 1, 2017, and connected to an underground storage tank, shall have under-dispenser containment if the installation is located 1000 feet or less from an existing community water system or an existing potable drinking water well.
(2) The under-dispenser containment shall:
(A) be liquid-tight on its sides, bottom, and at all penetrations;
(B) be compatible with the substance conveyed by the piping; and
(C) allow for visual inspection and access to the components in the containment system, or shall be continuously monitored for the presence of liquids.
(3) If an existing dispenser is replaced, the requirements of Subsection (b) shall apply to the new dispenser if any equipment used to connect the dispenser to the underground storage tank system is replaced. This equipment includes unburied flexible connectors, risers, and other transitional components that are beneath the dispenser and connect the dispenser to the product piping.
(c) The requirements of Subsections (a) and (b) shall not apply if the installation is located more than 1000 feet from an existing community water system or an existing potable drinking water well.
(1) The UST owner or operator shall provide to the Director documentation to show that the requirements of Subsections (a) and (b) to not apply to the installation. The documentation shall be provided at least 60 days before the beginning of the installation, and shall include:
(A) a detailed to-scale map of the proposed installation that demonstrates that no part of the installation is within 1000 feet of any community water system, potable drinking water well, or any well the owner or operator plans to install at the facility, and
(B) a certified statement by the owner or operator explaining who researched the existence of a community water system or potable drinking water well, how the research was conducted, and how the proposed installation qualifies for an exemption from the requirements of Subsections (a) and (b).
(d) To determine whether the requirements of Subsections (a) and (b) apply, the distance from the UST installation to an existing community water system or existing potable drinking water well shall be measured from the closest part of the new underground tank, piping, or motor fuel dispenser system to:
(1) the closest part of the nearest community water system, including:
(A) the location of the wellheads for groundwater and/or the location of the intake points for surface water;
(B) water lines, processing tanks, and water storage tanks; and
(C) water distribution/service lines under the control of the community water system operator, or
(2) the wellhead of the nearest existing potable drinking water well.
(e) If a new underground storage tank facility is installed, and is not within 1000 feet of an existing community water system or an existing potable drinking water well, the requirements of Subsections (a) and (b) apply if the owner or operator installs a potable drinking water well at the facility that is within 1000 feet of the underground tanks, piping, or motor fuel dispenser system, regardless of the sequence of installation of the UST system, dispenser system, and well.
(f) To meet the requirements of 40 CFR 280.20, all tanks and product piping that are installed or replaced as part of an underground storage tank system on or after January 1, 2017 shall be secondarily contained and use interstitial monitoring in accordance with 40 CFR 280.43(g).
(a) Owners and operators shall perform periodic inspections in accordance with 40 CFR 280.36. Inspections shall be conducted by or under the direction of the designated Class B operator. The Class B operator shall ensure that documentation of each inspection is kept and made available for review by the Director.
(b) The individual who conducts inspections to meet the requirements of 40 CFR 280.36(a)(1) or (a)(3) shall use the form "UST Operator Inspection- Utah" or another form approved by the Director.
(c) An UST facility whose tanks are properly temporarily closed according to 40 CFR 280.70 and R311-204-4 shall have an annual operator inspection.
(d) An owner or operator who conducts visual checks of tank top containment sumps and under dispenser containment sumps for compliance with piping leak detection in accordance with 40 CFR 280.43(g) shall conduct the visual checks monthly and report the results on the operator inspection form.
(a) A facility that normally has no employee or other responsible person on site, or is open to dispense fuel at times when no employee or responsible person is on site, shall have:
(1) a sign posted in a conspicuous place, giving the name and telephone number of the facility owner, operator, or local emergency responders, and
(2) an emergency shutoff device in a readily accessible location, if the facility dispenses fuel.
fees, hazardous substances, petroleum, underground storage tanks
January 3, 2017
March 27, 2017
19-6-105; 19-6-403; 19-6-408
For questions regarding the content or application of rules under Title R311, please contact the promulgating agency (Environmental Quality, Environmental Response and Remediation). A list of agencies with links to their homepages is available at http://www.utah.gov/government/agencylist.html or from http://www.rules.utah.gov/contact/agencycontacts.htm.